Originally Posted by somewhereinusa
If you want to drive to Indiana, you can have all the stuff I took out except for the condenser fans. Two of everything, worked when I took them off. No guarantee of anything.
thanks for the offer!! unfortunaterly yours are bluebird side mount specific.. I need a rear ceiling mount similar to the OP.. at least for engine powered..
Love your build!! the industrial look and esp the use of mini-splits for your A/C..
I fashioned 3 of those completely custom as part of a hybrid heat / cool in my house.. they are ducted and zoned through my existing home floor ducting... ..
only thing I can say is you may want to think about flexible pipe adapters between the unit and the pipes that go into your bus.. these units are Notorious for leaks at the flare connections..
they are also picky about their R410A charge so if you shortened or lengthened the piping.. (15 feet is used as reference)... you should adjust the charge accordingly..
Ive got a whole lab with these units in my basement.. LOL.. HVAC design is my second passion..
the beauty of those too is that they are soft start.. so no hard surges on your generator!